Koppla 0020 Apartment control unit for access control, energy metering and alarms. Features and advantages Wireless connection to Aperio type lock. Up to eight locks per Koppla 0020. Connect your lock to the system via Koppla 0020. Manages encrypted radio traffic with Aperio locks. Koppla 0020 can be paired with lock via a special software: Aperio Programming Application, PAP. Aptus cable 1 from control unit to door unit. Tamper switch from lock, logged to Multiaccess Styra. Possibility of programming a door to remain open for a chosen time. This can be done directly on the door. Specifications ELECTRICAL DATA Power supply V DC 24/12 Consumption Watts min 1,44 max 1,92 at 24V Amp min. 0.06 max. 0.08 for 24V ENVIRONMENT Temperature ˚C 5 to +35 Humidity % 10 to 90 PRODUCT DATA Number of A485 ports 1 (to control unit) LEDs for indication of communication status Yes LEDs indicate status of connected locks Yes Number of Koppla 0020 devices per Styra 3000 8 Number of locks per Styra 3000 8 (max 1 lock per door) Number of locks per Koppla 0020 8 Remote unlocking from Multiaccess Styra No Sensor detection, door open/closed No Remote upgrading via Multiaccess Styra Yes, partial Card data for connected locks Mifare:(Locks with MD in model name) Classic 1K & 4K 13,56 MHz 4 byte UID / 7 byte UID Serial number reading Sector readingEM:(Locks with EM in model name) 4102 & 4200 125 kHz RADIO Frequency band GHz 2,4 Number of channels 16 16 Reach, up to, m 15–25 Encryption AES 128-bit COMMUNICATION Communication with Styra 3000 RS 485 (A485) Communication with Aperio lock Radio DIMENSIONS, mm Height 81 Width 81 Depth 54 Net weight in kg 0,18 Close Get in touch and we will help you! Get contacts Similar products Koppla 4300Door unit for access, booking, entry phone, alarm and ene… Koppla 2100Apartment control unit for access control, energy meterin… Koppla 0010Door unit for radio communication with lock.